Home > Current Issue > Vol. 19, No. 1
[ Research Articles ]  
The International Journal of The Korea Institute of Ecological Architecture and Environment  Vol. 18, No. 6, pp.511  
Abbreviation: J. Korea Inst. Ecol. Archit. And Environ.  
ISSN: 2288968X (Print) 22889698 (Online)  
Print publication date 31 Dec 2018  
Received 28 Sep 2018 Revised 3 Dec 2018 Accepted 8 Dec 2018  
DOI: https://doi.org/10.12813/kieae.2018.18.6.005  
Statistical Analysis of Window Impacts on Cooling and Heating Energy Use in Single Family Residence Based on Climate Regions in U.S.A.  
Kim, Seongchan^{*} ; Shim, Euysup^{**}
 
*Corresponding author, Department of Engineering Technology, Western Illinois University, USA (skim7@wiu.edu)  
**Department of Technology, Illinois State University, USA (eshim@ilstu.edu)  
@ 2018 KIEAE Journal  
Abstract
Window area, location, and selection of glazing are a very important factor in reducing cooling and heating energy use of a building. The primary goal of this research is to investigate the effects of window design variables on annual cooling and heating energy use in a single residence based on climate regions in the United States using statistical analysis.
The methodologies used in this paper are building energy simulations, descriptive statistics, ttest, Latin Hypercube Sampling, and sensitivity analysis. Two groups of window variables are defined and simulated to explore the difference of the simulation results using Latin Hypercube Sampling and ttest. Then, the enter method as a regression model is used to investigate which group of data better predicted annual cooling and heating energy use. Lastly, Standard Regression Coefficients (SRCs) sensitivity indicator is used to determine if the influence of window parameters on cooling and heating energy use varies by different climate zone.
Ttest results show that the differences in simulation results between the two groups are not statistically significant. That means that simulations using less number of variables (Group B) can have similar accuracy than simulation with higher number of window variables (Group A). As a result of the regression models, average adjusted R^{2} is 0.886 for Group A and 0.933 for Group B. Therefore, the regression model using Group B is selected to determine the effect of each variable on energy use. According to SRCs from regression, the most sensitive design parameters for cooling energy use are SHGC, west and south facing windows, while Uvalue, north and west facing windows are the most sensitive window parameters for heating energy use.
Keywords: Glazing Thermal Properties, Window to Wall Ratio, Cooling and Heating Energy, Statistical Analysis 키워드: 유리창 열적특성, 창면적비, 냉난방 에너지, 통계분석 
Most of glazing systems in a building are made of highly conductive materials, so they are particularly prone to large heat gains and losses in buildings because of direct heat gain from solar radiation and heat transfer between outside and inside. It indicates that properly designed window is one of the important factors for an energy efficient building [1].
The International Energy Conservation Code (IECC) was created by the International Code Council in 2000. This code has been adopted by many US state and local governments to establish minimum design and construction requirements for energy efficiency.
In addition, IECC and ASHRAE (United States Heating, Refrigeration, Air Conditioning Engineers Association) define climate regions based on heating degree days, average temperature, precipitation to help builders to identify appropriate climate regions they build. So builders can decide the climatespecific construction guidelines from the IECC they should use.
The primary goal of this research is to investigate the effects of window design variables on annual cooling and heating energy in a single residence based on IECC requirements and different climate regions in the United States using the statistical analysis, which can provide references for window design.
According to Moorjani and Asadi [2], one of the most effective ways to reduce energy loss through the building envelope is to optimize thermal performance, area, and placement of the transparent parts of the building. Therefore, architects and general contractors should consider effective way of selecting and placing windows to control solar gains to reduce cooling energy use during the summer season, while reducing thermal losses during the winter season [3].
Although energy simulation can be useful in investigating heat gain or loss through windows, it requires significant time, resources, and technical expertise. In addition, building energy performance evaluation using the simulation tools is usually limited to complex buildings and applied in the later stages of design. For small building such as residences and lowrise apartment buildings, general contractors tend to use personal experience to make design decisions using the minimum requirements specified in the building code [4].
Janelle et al. [5] studied a new modeling approach to quantify building energy performance in the early design stage using multivariate linear regression model based on 27 building parameters for office buildings. This study suggested that the linear regression model can be the basis for effective decision support tools instead of energy simulation at the initial design stage.
One study also proposed to provide architects or general contractors with useful guidelines of the building design parameters to help them select building materials to construct an energyefficient house [6].
The methodologies used in this research are building energy simulations, descriptive statistics, ttest, Latin Hypercube Sampling (LHS), and sensitivity analysis including multivariate linear regression which determines the impacts of window design variables to building energy use. Fig. 1. shows the flowchart of the overall research methodology.
Fig. 1.
Research Methodology
Two specific questions to be answered through this study are as follows.
1) Is it possible to maintain or improve the predicted simulation results while minimizing the number of design variables?
The number of design variables for considerations should be minimized to provide simple and practical guideline for architects and general contractors. In order to select the efficient window design variables, two groups of window variables are defined in Table 1.
Window variables and associated sampling ranges used in the simulation
Group  Window Variables  Unit  Min.  Max. 

A  WWR^{1)}: South  %  5  90 
WWR: North  %  5  90  
WWR: West  %  5  90  
WWR: East  %  5  90  
Uvalue of window: South  W/°C·m^{2} (Btu/hr·ft^{2}·°F)^{2)} 
0.84 (0.15) 
4.50 (0.80) 

Uvalue of window: North  W/°C·m^{2} (Btu/hr·ft^{2}·°F) 
0.84 (0.15) 
4.50 (0.80) 

Uvalue of window: West  W/°C·m^{2} (Btu/hr·ft^{2}·°F) 
0.84 (0.15) 
4.50 (0.80) 

Uvalue of window: East  W/°C·m^{2} (Btu/hr·ft^{2}·°F) 
0.84 (0.15) 
4.50 (0.80) 

SHGC of window: South  N/A  0.25  0.75  
SHGC of window: North  N/A  0.25  0.75  
SHGC of window: West  N/A  0.25  0.75  
SHGC of window: East  N/A  0.25  0.75  
B  WWR: South  %  5  90 
WWR: North  %  5  90  
WWR: West  %  5  90  
WWR: East  %  5  90  
Uvalue of window: All orientations  W/°C·m^{2} (Btu/hr·ft^{2}·°F) 
0.84 (0.15) 
4.50 (0.80) 

SHGC of window: All orientations  N/A  0.25  0.75 
As seen in Table 1., twelve parameters are considered as window variables for Group A that were used in the previous research [6], and six parameters are used for Group B as an alternative. Since simulations of each group require extensive input for sensitivity analysis, Latin Hypercube Sampling (LHS) is used to develop the combinations of the window variables within the specified ranges for comprehensive simulation input files for sensitivity analysis. According to DominguezMunoz [7] et al., Latin Hypercube Sampling (LHS) is a common sampling technique for building energy simulations for a minimum number of simulations because each parameter has uniform distributions since all values within the specified range are considered equally probable design variables.
After performing simulations using a input variable from LHS, ttest was performed to investigate the difference between the results of two simulation groups. If the difference of simulation results between the two groups is not statistically significant (at 95% confidence level), it means that even with a small number of variables, it is possible to achieve the similar results with many variables. In addition, the comparison of regression results from two groups has been conducted to identify which group of regression model explains the simulation results better.
2) Does the window design variables have different effects on energy usage depending on climate conditions (climate regions)?
Because the cooling and heating energy demand is sensitive to different climate zones, simulations are conducted in six climate zones defined by ASHRAE [8]. Six climates are selected to explore the impact of local weather conditions, and they represent the average weather conditions of verycold (Minneapolis, MN); cold (Chicago, IL); mixedhumid (Atlanta, GA); hothumid (Houston, TX); hotdry (Phoenix, AZ); and marine (Los Angeles, CA) climates [9]. TMY3 weather data for each selected location were used for the simulations. The summary of the climate characteristics is shown in Table 2.
Climate Characteristics of the Six Selected Locations
Location  Climate Region  HDD65^{3)}  CDD65^{4)} 

Minneapolis, MN  Very Cold  7882  699 
Chicago, IL  Cold  6493  835 
Atlanta, GA  MixedHunid  2827  1810 
Houston, TX  HotHumid  1525  2893 
Phoenix, AZ  HotDry  1040  4355 
Los Angeles, CA  Marine  1286  682 
Sensitivity analysis is a study of the influence of independent variables on dependent variable in certain condition [10]. Therefore, sensitivity analysis has been used to study the effects of window design variables such as WWR, orientation and thermal properties of glazing on energy usage. There are two main approaches of sensitivity analysis: local sensitivity analysis and global sensitivity analysis. Local sensitivity analysis investigates the impact of one variable as keeping others fixed, while global sensitivity analysis uses all variables to investigate the relative impacts [6,11,12]. For this research, global sensitivity analysis has been used to study the impacts of all design parameters simultaneously on energy consumption.
In sensitivity analysis, regression is the most widely used method of building energy analysis because it is fast to compute and the results are easy to understand. From the regression model, many indicators can be used for the sensitivity indices such as SRC (Standard Regression Coefficients), PCC (Partial Correlation Coefficients), and their rank transformation (SRRC standardized rank regression coefficient), and partial rank correlation coefficient (PRCC) [13]. One study has applied SRC indicator to determine the main variables affecting the maximum cooling load of a perimeter zone in a threestory office in southern Spain [14].
For this research, SRC sensitivity indicator is also used to study the influence of window parameters on cooling and heating energy use in different climate zones.
Basecase simulation model is a singlefamily residence based on U.S. Census Beaureu and IECC requirements of wall, floor, and roof assembly, and HVAC system efficiency specifically for singlefamily residence.
A 232 m^{2} (2,500 ft^{2}) singlefamily residence is considered as the basis for this study based on U.S. Census Beaureu [15]. The basecase house is assumed to have lightweight woodframe construction with 5 cm x 10 cm (2 inches x 4 inches) wall studs spaced at 40.6 cm (16 inches) oncenter and 5 cm x 15 cm (2 inches x 6 inches) ceiling joists/roof rafters spaced at 61 cm (24 inches) oncenter, a 10 cm (4inch) slabongrade floor, and an unconditionedvented attic space. The basecase house has the 2015 IECC^{5)} specified climatespecific exterior wall assembly (3.52 m^{2}·°C/w (R20)) and ceiling assembly (8.63 m^{2}·°C/w (R49)), slab perimeter insulation (0.61 m (2 ft) 1.76 m^{2}·°C/w (R10) perimeter with 0.88 m^{2}·°C/w (R5) gap). The basecase HVAC system includes a SEER^{6)} 13 central airconditioner with a 78% AFUE^{7)} furnace conforming to the 2015 IECC. The heating and cooling setpoints are 21.7°C (71 ºF) for the winter and 24.4°C (76 ºF) for the summer without setback temperature.
For the simulation, BEopt simulation program ver. 2.7 was used. BEopt stands for Building Energy Optimization, and has been developed by the National Renewable Energy Laboratory (NREL) in support of the U. S. Department of Energy (DOE). BEopt software is specially developed for building energy simulation of residence to utilize EnergyPlus simulation engine, and provides detailed simulation analysis to evaluate residential building energy consumptions [16].
The results of this study include the follows: 1) simulation results of base case house in six selected locations, 2) ttest results between Group A and Group B as explained in Table 1., 3) comparison of regression models between Group A and Group B, and 4) SRC (Standard Regression Coefficients) results of a selected regression model.
From the BEopt output, the thermal energy use and electricity use are investigated on an annual basis. Fig. 2. to Fig. 6. show the annual total energy use, electricity use and thermal energy use for the six selected locations including: 1) Minneapolis, MN, 2) Chicago, IL, 3) Atlanta, GA, 4) Houston, TX, 5) Phoenix, AZ, and 6) Los Angeles, CA. Table 3. indicates the case number in X axis in Figures from 2. to 6.
Fig. 2.
Total energy use for six selected locations
Fig. 3.
Cooling and heating energy use for six selected locations
Fig. 4.
Electrical energy use for six selected locations
Fig. 5.
Electrical energy use of cooling and heating for six selected locations
Fig. 6.
Thermal energy use for six selected locations
Name of City in Figures from 2. to 6.
Case Number  City Name 

1  Minneapolis, MN 
2  Chicago, IL 
3  Atlanta, GA 
4  Huston, TX 
5  Pheonix, AZ 
6  Los Angeles, CA 
Fig. 2. shows total energy use for a year (kWh/year) including cooling and heating, fan, lighting, and other appliances. Fig. 3. excludes the energy use of lighting and other appliances from Fig. 2. and shows only cooling and heating energy use since energy uses of lighting and other appliances show the same in each region.
Fig. 4. shows electrical energy use including cooling, fan, lighting, and other appliances, and Fig. 5. shows only cooling and fan energy for heating and cooling from electrical energy use.
Lastly, Fig. 6. shows thermal energy use including heating and domestic hot water energy use.
More energy use for heating was observed specially in Minnesota and Illinois, and more energy usage for cooling was observed specially in Arizona and Texas, which conform to the heating degree days and cooling degree days (Table 2.). These variations in cooling and heating energy are a direct indication of the local climate features such as long winter period of Minnesota and Illinois and long summer period of Arizona and Texas. The relatively mild climate condition in California and Georgia shows that cooling and heating energy use has been used relatively less than other regions. In addition, lighting and other appliances show a large share of electrical energy use.
Independent twosample ttest was conducted to explore the difference in the means of the simulation results from Group A which used 12 window variables and Group B which used 6 window variables. The sample size of Group A and Group B is 120 (n=120) and 80 (n=80), respectively. The sample size was determined as recommended by Latin Hypercube Sampling method which uses 10 times the number of variables [17].
For statistical analysis, the null hypothesis is that there is no difference between the means of two simulation groups. Table 4. shows the results of ttest for annual cooling and heating energy use. As shown in Table 4., the difference in annual cooling and heating energy use between the two groups is not statistically significant at 95% confidence level. Therefore, the null hypothesis fails to be rejected because the pvalue is larger than 0.05. This results mean that even though the simulations are performed using less number of window variables, it can have similar accuracy to simulations using higher number of window variables.
Ttest results between group A and group B of the Six Selected Locations
Location  Mean  t  p  

Group A (n=120) 
Group B (n=80) 

Cooling Energy Use (kWh/year)  
MN  1424.1  1437.1  .165  .869 
IL  1679.4  1690.0  .127  .899 
GA  3840.1  3850.4  .074  .941 
TX  6031.4  6049.8  .104  .917 
AZ  10518.0  10548.3  .103  .918 
CA  1183.2  1200.2  .205  .838 
Heating Energy Use (kWh/year)  
MN  44266 (1510.4)^{8)} 
44492 (1518.1) 
.200  .841 
IL  35069 (1196.5) 
35182 (1200.4) 
.108  .914 
GA  11076 (377.9) 
11304 (385.7) 
.459  .647 
TX  4205 (143.5) 
4361 (148.8) 
.641  .523 
AZ  1447 (49.4) 
1655 (56.5) 
1.378  .171 
CA  2090 (71.3) 
2414 (82.4) 
1.474  .143 
Regression analysis is also performed to investigate which group of data better predicts annual cooling and annual heating energy use. For the regression model, the enter method was used, which all independent variables are simultaneously entered into the regression model. This method is an appropriate method for analyzing the small numbers of independent variables or when the researcher does not know which independent variables can yield the best regression equation [18].
Since this research investigates the effect of all the variables used in this study and the number of variables is relatively small, the enter method was considered appropriate for the multivariate regression modeling. Table 5. shows the adjusted R^{2} which indicates how closely data such as WWRs, SHGC and Uvalue can explain annual cooling and annual heating energy use. It was found that the overall regression models show a good fit. The multiple linear regression in each location yields an adjusted R^{2} from 0.932 to 0.960 in Group A and from 0.918 and 0.966 in Group B for annual cooling energy. The regression for annual heating energy yields an adjusted R^{2} from 0.798 to 0.838 in Group A and from 0.896 to 0.944 in Group B. The average adjusted R^{2} for both cooling and heating energy is 0.886 for Group A and 0.933 for Group B. Therefore, the regression model using Group B is selected to investigate the effect of each variable on energy use. In addition, the value of DurbinWatson in all regression models is close to 2, which means that there is no autocorrelation between data.
Results of adjusted R square of group A and group B of the Six Selected Locations
Location  Group A  Group B  

Adjusted R Square  DurbinWatson  Adjusted R Square  DurbinWatson  
Cooling Energy Use 
MN  0.956  2.068  0.927  1.775 
IL  0.950  1.804  0.931  1.768  
GA  0.954  2.043  0.942  1.823  
TX  0.956  2.047  0.950  1.873  
AZ  0.960  2.044  0.966  1.996  
CA  0.932  1.967  0.918  1.700  
Heating Energy Use 
MN  0.838  1.951  0.944  1.749 
IL  0.832  1.967  0.944  1.771  
GA  0.818  1.951  0.941  1.782  
TX  0.821  1.967  0.936  1.760  
AZ  0.811  1.927  0.898  1.918  
CA  0.798  1.889  0.896  1.967 
Tables 6. and 7. describe the influence of each variable on annual cooling and annual heating energy use in six different locations.
Standardized Regression Coefficient (SRC) is used to represent relative contributions of each variable to annual cooling and heating energy variability in each region. T and pvalue are also presented to check statistically significance of each variable.
It was found that window design variable that has the most important effect on cooling energy usage is SHGC which is consistent across all locations according to the SRC in Table 6. For example, California shows the highest sensitivity to SHGC followed closely by Illinois. On the other hand, the Uvalue of the window is not statistically significant (p>0.05) in relatively cold regions such as Minnesota and Illinois. Uvalue in relatively hot climate zone such as Texas and Arizona is statistically significant (p<0.05), but it has less impact on the annual cooling energy use than other variables. Therefore, in Texas and Arizona where the cooling load is relatively high, SHGC is more important than the Uvalue in window selection. Not surprisingly, it has been found that as WWR increases, the cooling energy consumption increases. The SRCs were also observed to determine which orientation of WWR has more influence on cooling energy consumption. It is found that WWR in the west and east has a greater effect on the use of cooling energy than the north and south. This is due to excessive amount of solar radiation at low angle coming from the east and west sides in the morning and afternoon during summer. Therefore, it is appropriate to select a low SGHC window with a smaller window area in the east and west sides specially in hot climate zone (cooling dominated region) in order to reduce cooling energy.
Standardized Regression Coefficient (SRC) of each variable for annual cooling energy use in six locations.
Location  Independent Variables  Standardized Coefficients (SRC)  t  Sig. 

MN  SHGC  .757  23.696  .000 
WWR West  .436  13.585  .000  
WWR East  .385  11.645  .000  
WWR South  .252  7.922  .000  
WWR North  .113  3.446  .001  
Uvalue  .012  .384  .702  
IL  SHGC  .762  24.465  .000 
WWR West  .411  13.135  .000  
WWR East  .405  12.594  .000  
WWR South  .250  8.050  .000  
WWR North  .126  3.917  .000  
Uvalue  .022  .694  .490  
GA  SHGC  .756  26.373  .000 
WWR West  .422  14.634  .000  
WWR East  .421  14.205  .000  
WWR South  .247  8.625  .000  
WWR North  .146  4.952  .000  
Uvalue  .041  1.447  .152  
TX  SHGC  .736  27.874  .000 
WWR East  .417  15.295  .000  
WWR West  .417  15.715  .000  
WWR South  .295  11.196  .000  
WWR North  .161  5.935  .000  
Uvalue  .104  3.936  .000  
AZ  SHGC  .662  30.153  .000 
WWR West  .461  20.911  .000  
WWR East  .423  18.647  .000  
WWR South  .309  14.106  .000  
Uvalue  .290  13.223  .000  
WWR North  .162  7.183  .000  
CA  SHGC  .776  22.873  .000 
WWR West  .387  11.352  .000  
WWR East  .282  8.056  .000  
WWR South  .209  6.165  .000  
WWR North  .045  1.281  .204  
Uvalue  .244  7.192  .000 
As shown in Table 7., it was found that Uvalue is the most influential on the amount of heating energy usage. Furthermore, both SHGC and Uvalue are statistically significant (p<0.05), and these two variables affect the heating energy demands more than other WWRs. This results show different patterns from the results of cooling energy use. For cold climate zones (heating dominated region) such as Minneapolis and Illinois, high SHGC and low Uvalue should be considered more than other variables to reduce the heating energy demands.
Standardized Regression Coefficient (SRC) of each variable for annual heating energy use in six locations.
Location  Independent Variables  Standardized Coefficients (SRC)  t  Sig. 

MN  Uvalue  .800  28.571  .000 
WWR North  .236  8.191  .000  
WWR West  .139  4.942  .000  
WWR East  .114  3.935  .000  
WWR South  .041  1.450  .151  
SHGC  .296  10.559  .000  
IL  Uvalue  .799  28.426  .000 
WWR North  .231  7.984  .000  
WWR West  .143  5.053  .000  
WWR East  .109  3.751  .000  
WWR South  .051  1.809  .075  
SHGC  .301  10.685  .000  
GA  Uvalue  .766  26.678  .000 
WWR North  .233  7.846  .000  
WWR West  .120  4.145  .000  
WWR East  .075  2.533  .013  
WWR South  .015  .521  .604  
SHGC  .378  13.147  .000  
TX  Uvalue  .764  25.517  .000 
WWR North  .234  7.584  .000  
WWR West  .125  4.141  .000  
WWR East  .092  2.980  .004  
WWR South  .014  .471  .639  
SHGC  .371  12.376  .000  
AZ  Uvalue  .696  18.404  .000 
WWR North  .268  6.875  .000  
WWR West  .126  3.320  .001  
WWR East  .087  2.229  .029  
WWR South  .030  .790  .432  
SHGC  .414  10.934  .000  
CA  Uvalue  .680  17.831  .000 
WWR North  .230  5.848  .000  
WWR West  .074  1.923  .058  
WWR East  .044  1.121  .266  
WWR South  .013  .336  .738  
SHGC  .484  12.682  .000 
For WWR, window areas in the north and west are more influential to the heating energy use than other orientations. It is because there is less opportunity to receive solar radiation than other orientations of windows while there is more conduction heat loss due to large window areas at the same time. This results in more heating energy consumption because of large window areas in the north and west sides. It is also found that WWRs on the south side is not statistically significant (p>0.05) for all locations. For the window layout, consideration of WWR of the north, west and east is more important than that of the south to reduce the heating energy use.
Building simulation can accurately predict building energy use, but it is difficult to be utilized by architects and general contractors because it requires higher level of engineering expertise. The purpose of this study is to present the data that can be referenced by the architects and general contractors that investigates the effect of window properties including SHGC and Uvalue, and WWRs on the energy consumptions in six climate regions representing the United States.
In order to obtain the data for the statistical analysis, the extensive numbers of simulations using the average size of the residence in the U.S. were performed with BEopt simulation program. For simulations, two groups with different numbers of window variables were used.
To study the optimum numbers of window variables, ttest was performed using the results from two groups.
Ttest results show that the difference in simulations results between the two groups are not statistically significant. Then, a regression model of two groups is developed to identify a better fit to the simulation results. All adjusted R^{2} values obtained from the multivariate regressions show a good fit to the simulation results. However, the average adjusted R^{2} is 0.886 for Group A and 0.933 for Group B, so standardized regression coefficients (SRCs) generated in Group B are used for sensitivity analysis. This results suggest that the regression model can be developed using a reduced numbers of variables, and also can be useful for the architect and general contractor for window design considerations.
According to SRCs from the regression, the most sensitive design parameters for cooling energy use are SHGC and west and south facing windows, while Uvalue and north and west facing windows are the most sensitive window parameters for heating energy use.
The results of this research considered the relative importance of window design variables based on different climate regions for single family residence, and have limitations for builders to apply to have window designs specifically. Future ongoing research needs to perform indepth analysis to provide detailed range of appropriate window thermal properties varying window area and construction costs based on climate regions. This combination of results can provide builders with guideline to consider better window design decisions.
References
1.  Samar, J, Salman, A, Thermal and economic windows design for different climate zones, Energy and Buildings, (2011), 43, p32083215. 
2.  Vahid, M, Somayeh, A, Assessing the effects of glazing type on optimum dimension of windows in office buildings, 50th ASC Annual International Conference Proceedings, 2014, Oct. 
3.  Andrea, G, Giovanni, P, Francesca, C, Piercarlo, R, Paolo, B, Analysis and modelling of window and glazing systems energy performance for a well insulated residential building, Energy and Buildings, (2011), 43, p10301037. 
4.  Mora, R, Bedard, C, Rivard, H, A geometric modelling framework for conceptual structural design from early digital architectural models, Advanced Engineering Informatics, (2008), 22, p25470. 
5.  Janelle, H, Joseph, D, David, H, Ranji, R, Multivariate regression as an energy assessment tool in early building design, Building and Environment, (2012), 57, p165175. 
6.  Yusuf, Y, Koray, K, Türkan, G, Zeynep, A, An approach for developing sensitive design parameter guidelines to reduce the energy requirements of lowrise apartment buildings, Applied Energy, (2012), 93, p337347. 
7.  DominguezMunoz, F, CejudoLopez, MJ, CarrilloAndres, A, Uncertainty in peak cooling load calculations, Energy Build, (2010), 42, p10108. 
8.  ASHRAE, ASHRAE 90.12007 Energy standard for buildings except lowRise residential buildings, Atlanta, GA, American Society of Heating, Refrigeration, and AirConditioning Engineers, (2007). 
9.  Mini, M, An analysis of offgrid, offpipe housing in six U.S. climates, Ph.D. Dissertation, Texas A&M University, (2009). 
10.  Andrea, Saltelli, et al. , Sensitivity Analysis in Practice, John Wiley & Sons, UK, (2004). 
11.  Heiselberg, P, Brohus, H, Hesselholt, A, Rasmussen, H, Seinre, E, Thomas, S, Application of sensitivity analysis in design of sustainable buildings, Renew Energy, (2009), 34, p20306. 
12.  Yıldız, Y, Arsan, DZ, Identification of the building parameters that influence heating and cooling energy loads for apartment buildings in hothumid climates, Energy, (2011), 36, p428796. 
13.  Wei, T, A review of sensitivity analysis methods in building energy analysis, Renewable and Sustainable Energy Reviews, (2013), 20, p411419. 
14.  Ilaria, B, Vincenzoc, C, Analysis of the building energy balance to investigate the effect of thermal insulation in summer conditions, Energy and Buildings, (2012), 52, p168180. 
15.  U.S. Census Beaureu, Highlights of Annual 2016 Characteristics of New Housing, Available at https://www.census.gov/construction/chars/highlights.html (accessed Sep 1, 2017) (2016). 
16.  NREL (National Renewable Energy Laboratory), BEopt, Available at https://beopt.nrel.gov/ (accessed Nov 15, 2017) (2017). 
17.  Simlab, Software package for uncertainty and sensitivity analysis. Joint Research Centre of the European Commission, Available at https://ec.europa.eu/jrc/en/samo/simla (accessed Oct 2, 2017) (2017). 
18.  IBM Corp., Released 2011. IBM SPSS Statistics for Windows, Version 20.0, Armonk, NY, IBM Corp. 